Supply, install and commission
MagnaGrand IP and mixer
We were asked to specify twin foul water pumps capable of 6l/s at a 12m head due to a two storey basement excavation. The pumps required large solids clearance due to the nature of the multi-occupancy dwelling. A mixer would be needed to prevent the build-up of floating fats and solids. We were asked to plan the route through the two storey basement for the rising main to run.
• Twin guide rail mounted pumps were installed with an 80mm solids clearance into a concrete sump 10m long, 2.4m wide and 3.5m deep.
• The pumps have an 80mm clear passage through the body of the pump, reducing the chances of blockages.